W415-0809 / A / 05.10.10
2.1 GENERAL INSTRUCTIONS
Thoroughly clean the chimney, ﬂ ue and existing appliance before installing the new appliance into it. Do not
burn solid fuels in any appliance that is equipped with this gas log set.
The installation of this appliance must conform with local codes or in the absence of local codes with the
National fuel gas code ANSI Z.223.1 / NFPA 54.
Do not operate appliance in the presence of gasoline or other ﬂ ammable liquids and vapours. Keep area clear
of other combustible materials. The appliance and its shut off must be disconnected from the gas supply piping
system before any pressure testing of the system is done.
Installation practices vary from region to region and it is important to know the speciﬁ cs that apply to your area,
For example: in Massachusetts State:
• The appliance off valve must be a “T” handle gas cock.
• The ﬂ exible connector must not be longer than 36 inches.
• The appliance is not approved for installation in a bedroom or bathroom unless the appliance is a
direct vent sealed combustion product.
• Unvented room appliance shall be installed in accordance with 527 CMR 30.00 and 248 CMR 3.00
• Sellers of unvented propane or natural gas-ﬁ red space/room appliances shall provide to each
purchaser a copy of 527 CMR 30.00 upon the sale of the appliance from
• A carbon monoxide detector is required in all rooms containing gas ﬁ red appliances.
This appliance may be installed in an aftermarket, permanently located, manufactured (mobile) home, where
not prohibited by local codes.
ALWAYS LIGHT THE PILOT WHETHER FOR THE FIRST TIME OR IF THE GAS SUPPLY HAS RAN OUT,
WITH THE GLASS DOOR OPENED OR REMOVED.
PROVIDE ADEQUATE CLEARANCE FOR SERVICING AND OPERATING THE APPLIANCE.
PROVIDE ADEQUATE VENTILATION.
NEVER OBSTRUCT THE FRONT OPENING OF THE APPLIANCE.
OBJECTS PLACED IN FRONT OF THE APPLIANCE MUST BE KEPT A MINIMUM OF 48” FROM THE
FRONT FACE OF THE UNIT.
SURFACES AROUND AND ESPECIALLY ABOVE THE APPLIANCE CAN BECOME HOT. AVOID CONTACT
WHEN THE APPLIANCE IS OPERATING.
FIRE RISK. EXPLOSION HAZARD.
HIGH PRESSURE WILL DAMAGE VALVE. DISCONNECT GAS SUPPLY PIPING BEFORE PRESSURE TESTING
GAS LINE AT TEST PRESSURES ABOVE 1/2 PSIG. CLOSE THE MANUAL SHUT-OFF VALVE BEFORE
PRESSURE TESTING GAS LINE AT TEST PRESSURES EQUAL TO OR LESS THAN 1/2 PSIG.
USE ONLY WOLF STEEL APPROVED OPTIONAL ACCESSORIES AND REPLACEMENT PARTS WITH THIS APPLIANCE.
USING NON-LISTED ACCESSORIES (BLOWERS, DOORS, LOUVRES, TRIMS, GAS COMPONENTS, VENTING
COMPONENTS, ETC.) COULD RESULT IN A SAFETY HAZARD AND WILL VOID THE WARRANTY AND CERTIFICATION.